Fitzroy Falls, NSW
Fitzroy Falls Off-Grid Ground Mounting and On-Grid Integrated System
Install – 3 October 2017
System Size – 24kW
Panels – Trina 300W x 20
Our Client in Fitzroy Falls spent millions on building a near like castle house that included the state of the art architecture, tennis courts, top of the range heating and cooling systems, swimming pools and more. Our client just required one more thing to complete his dream house and that was to be able to go green through using renewable energy and install a reliable top of the range solar system.
Of course, Space Solar Service took on this challenge and saw this as an opportunity to offer a system installation that not many solar companies can provide. To maximise optimum angle and position to capture maximum light, a massive 24kW ground mounted/on grid integrated solar system was installed by Space Solars installed Accredited CEC installers. Using, 80 x Trina Solar /TSM300 + 2 x Fronius Primo 8.0 + 2 x Fronius Primo3.0 + 9 x BYD battery with a rated capacity of 51.2v/50Ah + 2 x Victron / Quatrro 48/10000/140 with a total rated capacity of 20 KVA/280A battery charger.
- PV Inverter System
|1||Brand & Model||Fronius / Primo 8.0||Fronius / Primo3.0|
|2||Rated Capacity||8.0 KW||3.0 KW|
|4||Total Capacity||22.0 KW||11KW per phase|
- Battery System
|1||Brand & Model||BYD / Li-Ion U3A1-50P-A|
|4||Total Capacity||51.2v/450Ah||Two phases share|
- Battery Inverter & Backup System
|1||Brand & Model||Victron / Quatrro 48/10000/140|
|2||Rated Capacity||10 KVA /140A battery charger||20KW Peak|
|3||Quantity Installed||2||1 per phase|
|4||Total Capacity||20 KVA/280A battery charger||10KVA/140A per phase|
The client in Fitzroy Falls installed a huge air conditioning system that his on-grid 2 phase house hold would not be able to support. Installing this 24kW ground mounting system with the ability to go on-grid was the ideal solution to allow his air conditioning system to function when the solar generation is producing. In the event of a blackout, the customer has the backup battery function that will discharge to allow his air conditioning system to function at all times. The customer is able to revert back to the grid power in the case were solar production is insufficient (cloudy days or rainy days) keeping the clients house always powered.